UNE 21031 (Construction & tests)
Low Voltage Directive: 2014/35 / EU
CPR Regulation (EU) No 305/2011:
Reaction to fire (Eca)
Technical characteristics & performances
- Bunched conductor (class 5) mm2
- Maximum service temperature: 70ºC / 160ºC
- 300 / 500 V C.A.
- Eca (reaction to fire)
- Flame retardant
Uses and applications
- Panel and appliance wiring
- Control & command
- Industral use
- Mobile service
UNE 21031 (Construction and tests)
Flexible, annealed, plain copper conductor, class 5 based on standard IEC 60228. Suitable for mobile service.
Polyvinyl chloride insulation (PVC) type TI2 acc. to EN 50363-3.
- ASSEMBLY OF CONDUCTORS:
The cores are cabled helically.
- OUTER SHEATH:
Polyvinyl chloride Sheath (PVC) type TM2 acc. to EN 50363-4-1
Multicore cable (From 6 to 61 cores / s: 1 mm2).
Core identification is according to standard EN 50334.
All cores in the cable are black and have an inscription along the whole length of them, except one core
which is coloured green/yellow (this core isn´t numbered).
The inscription is composed of marks repeated at regular intervals along the whole length of the core.
Each mark comprises:
- A reference number beginning at 1 in Arabic numerals;
- A dash which underlines this number and indicates the direction in which the number should be read.
Normal operation temperature:
Short-circuit temperature (5 s max):
- Reaction to fire: Eca (EN 50575:2014+A1:2016)
Flame retardant: EN 60332-1-2; IEC 60332-1 (H≤425 mm)
For covered range (+ information), please check out "CPR/DoP" section in our website.
*The packaging labels of these cables include the CE marking according to the CPR Regulation ((EU) Nº 305/2011) articles 8 and 9.
Type of installation:
Multicore cable for control circuits in industrial installations.
These cables are suitable for medium mechanical stress in damp and wet environments such as refrigerators, washing machines, spin dryers and other appliances, as long as it meets applicable equipment specifications. These cables are also suited for cooking and heating apparatus, provided that the cable does not come into direct contact with the hot parts of the apparatus or with any other heat source.
Mobile service- Duty: Ordinary
Presence of water - condition AD2.
Corrosive or polluting substances - condition AF3.
Intermittent and temporary periods of shord duration. Use outdoors for temporary periods of short duration.