IEC 60502-1, UNE 21123-2
(Construction and tests)
LOW VOLTAGE DIRECTIVE: 2014/35 / EU
CPR Regulation (EU) No 305/2011:
Reaction to fire (Eca)
Technical characteristics & performances
- Bunched conductor (class 5) mm2
- Maximum service temperature: 90ºC / 250ºC
- 0,6/1 (1,2) kV C.A
- Low temperature resistance
- Easy peeling / easy strip
- Protection against Electromagnetic disturbances
- Eca (reaction to fire)
- Flame retardant
Uses and applications
- Control & command
- Distribution networks
- Industral use
- Exterior lighting
- Outdoor use
RC4V-K 0,6/1 kV
IEC 60502-1, UNE 21123-2 (Construction and tests)
Flexible, annealed, plain copper conductor, class 5 based on International standard IEC 60228.
Cross-linked polyethylene (XLPE) according to International standard IEC 60502-1
- ASSEMBLY OF CONDUCTORS:
In multicore cables, the cores are cabled helically.
Polyester tape + copper braid with a coverage greater than 60%.
NOTE: Other types of materials or coverages, on request.
PVC type ST2 according to International standard IEC 60502-1.
Identification of cores HD 308 S2:
2x - brown and blue
3x - brown, black and gray
3G - brown, blue and yellow / green
4x - brown, black, gray, blue
4G - brown, black, gray, yellow / green
5G - brown, black, gray, blue, yellow / green
Normal operation temperature:
Short-circuit temperature (5 s max):
Oversheath: Black / Insulation: HD 308 S2
- Reaction to fire: Eca (EN 50575:2014+A1:2016)
• EN 60332-1-2; IEC 60332-1 (H≤425 mm) Flame retardant
For covered range (+ information), please check out "CPR/DoP" section in our website.
*The packaging labels of these cables include the CE marking according to the CPR Regulation ((EU) Nº 305/2011) articles 8 and 9.
Type of installation:
Barryflex SHIELD RC4V-K 0,6/1 kV control & instrumentation cables are specially indicated for its use in distribution networks, power stations, industries or buildings and electrical installations where a protection against electromagnetic interference is necessary (EMC).
“ (...)For electrical energy transport and distribution, distribution networks, protected or not. For indoor and outdoor installations. Non suitable for facilities of feeding of submerged pumps. (...)”