EN 50525-2-51 (Construction & tests)
IEC 60332-1-2 (Flame retardant)
Low Voltage Directive: 2014/35 / EU
Technical characteristics & performances
- Bunched conductor (class 5) mm2
- Maximum service temperature: 70ºC / 160ºC
- 300 / 500 V C.A.
- Oil resistance
- Easy peeling / easy strip
- Flame retardant
Uses and applications
- Panel and appliance wiring
- Control & command
- Industral use
- Mobile service
EN 50525-2-51 (Construction and tests)
Oil resistant control cables with thermoplastic PVC insulation.
Flexible, annealed, plain copper conductor, class 5 based on standard IEC 60228. Suitable for mobile service.
Polyvinyl chloride insulation (PVC) type TI2 acc. to EN 50363-3.
- ASSEMBLY OF CONDUCTORS:
The cores are twisted together.
- OUTER SHEATH:
Polyvinyl chloride Sheath (PVC) type TM5 acc. to EN 50363-4-1
Identification of cores HD 308 S2:
2x - brown and blue
3x - brown, black and gray
3G - brown, blue and yellow / green
4x - brown, black, gray, blue
4G - brown, black, gray, yellow / green
5G - brown, black, gray, blue, yellow / green
Normal operation temperature:
Short-circuit temperature (5 s max):
- Flame retardant: EN 60332-1-2; IEC 60332-1 (H≤425 mm)
Type of installation:
Flexible power, process control and instrumentation cable for industry and machinery environment.
Applications requiring resistance to general purpose mineral oils. For the interconnection of parts of equipment used for manufacturing including machines tool.
These cables are mineral oils resistant (general use), but they are not suitable for staying in continuous oil inmersion. They can be indoors and outdoors (for temporary periods of short duration). The contamination by hydrocarbons acid and alkalis must be avoided and the cables must be protected from mechanical damage.
Where the cables are not required to move in use, installation in conduit, trunking, etc. is advised.
Mobile service- Duty: Ordinary
Presence of water - condition AD2.
Corrosive or polluting substances - condition AF3.
Intermittent and temporary periods of shord duration. Use outdoors for temporary periods of short duration.
The 60ºC maximum conductor operating temperature of these cables takes into account the stated recommendations for use. If however the cables are to used inside equipment or the like were no contact with skin can be guaranteed then the cables are suitable for a maximum conductor operating temperature of 70ºC.