IEC 60502-1, UNE 21123-2
(Construction and tests)
LOW VOLTAGE DIRECTIVE: 2014/35 / EU
CPR Regulation (EU) No 305/2011:
Reaction to fire (Eca)
(Naval- Steel Ships)
(Naval- Steel Ships)
Technical characteristics & performances
- Bunched conductor (class 5) mm2
- Maximum service temperature: 90ºC / 250ºC
- 0,6/1 (1,2) kV C.A
- Low temperature resistance
- Easy peeling / easy strip
- Eca (reaction to fire)
- Flame retardant
Uses and applications
- Distribution networks
- Industral use
- Exterior lighting
- Steel ships
- Outdoor use
RV-K 0,6/1 kV
IEC 60502-1, UNE 21123-2 (Construction and tests)
Flexible, annealed, plain copper conductor, class 5 based on International standard IEC 60228.
Cross-linked polyethylene (XLPE) according to International standard IEC 60502-1
- ASSEMBLY OF CONDUCTORS:
In multicore cables, the cores are cabled helically.
Optional for multicore cables. Extruded. Thermoplastic material, suitable for the operating temperature of the cable and compatible with the insulating and sheathing material.
PVC type ST2 according to International standard IEC 60502-1.
Identification of cores HD 308 S2:
2x - brown and blue
3x - brown, black and gray
3G - brown, blue and yellow / green
4x - brown, black, gray, blue
4G - brown, black, gray, yellow / green
5G - brown, black, gray, blue, yellow / green
Normal operation temperature:
Short-circuit temperature (5 s max):
- Reaction to fire: Eca (EN 50575:2014+A1:2016)
• EN 60332-1-2; IEC 60332-1 (H≤425 mm) Flame retardant
For covered range (+ information), please check out "CPR/DoP" section in our website.
*The packaging labels of these cables include the CE marking according to the CPR Regulation ((EU) Nº 305/2011) articles 8 and 9.
Type of installation:
Barryflex RV-K 0,6/1 kV power cables are specially indicated for its use in distribution networks, power stations, industries or buildings and electrical installations in ships.
“ (...)For electrical energy transport and distribution, distribution networks, protected or not. For indoor and outdoor installations. Non suitable for facilities of feeding of submerged pumps. (...)” (UNE 21123-2)